may be connected to any 24 volt Fire Alarm Control Panel (FACP)
Primary applications include Notification Appliance Circuit (NAC) expansion (supports ADA requirements) and providing auxiliary power to support system accessories.
This model replaces AL600ULADA
Input: Power input 120VAC 60 Hz, 4 amp. Two (2) Class A, Style Z or two (2) Class B, Style W, X, Y FACP inputs. Two (2) NC dry contact trigger inputs.
Output: 24VDC @ 6.5 amp max total alarm current. 2.5 amp max current per output. Separate 1.0 amp auxiliary output. Two (2) outputs may be paralleled for more power on an indicating circuit (see 02 Application Guide). Programmable supervised indicating circuit outputs: Four (4) Class B, Style W, X, Y or Two (2) Class A, Style Z or One (1) Class A, Style Z and Two (2) Class B, Style W, X, Y (see 02 Application Guide). Thermal and short circuit protection with auto reset.
Battery Backup: Charging voltage is 26.2-26.4VDC. Built-in charger for sealed lead acid or gel type batteries. Automatic switchover to stand-by battery when AC Fails. Zero voltage drop when switching over to battery backup.
Common trouble input and output for external trouble signals tie-in